دایره المعارف تاسیسات برق (اطلاعات عمومی برق)
All rotating electrical machines generate heat as a result of the electrical and mechanical losses inside the machine. Losses are high during starting or dynamic braking. Also, losses usually increase with increased loading. Cooling is necessary to continuously transfer the heat to a cooling medium, such as the air. The different methods of cooling rotating machines are classified in the standards IEC 34.6 and AS 1359.21.
For AC induction motors, cooling air is usually circulated internally and externally by one or more fans mounted on the rotor shaft. To allow for operation of the machine in either direction of rotation, fans are usually of the bi-directional type and made of a strong plastic material, aluminum, or steel.
In addition, the external frames of the motor are usually provided with cooling ribs to increase the surface area for heat radiation.
The most common type of AC motor is the totally enclosed fan cooled (TEFC) motor, which is provided with an external forced cooling fan mounted on the non-drive end (NDE) of the shaft, with cooling ribs running axially along the outer surface of the motor frame. These are designed to keep the air flow close to the surface of the motor along its entire length, thus improving the cooling and self-cleaning of the ribs. An air-gap is usually left between the ribs and the fan cover for this purpose.
Internally, on smaller TEFC motors, the rotor
end-rings are usually constructed with ribs to provide additional
agitation of the internal air for even distribution of temperature and
to allow the radiation of heat from the end shields and frame.
Special precautions need to be taken when standard TEFC induction motors are used with AC variable speed drives, powered by VVVF converters. For operation at speeds below the rated frequency of 50 Hz, the shaft mounted fan cooling efficiency is lost. For constant torque loads, it is sometimes necessary to install a separately powered forced cooling fan (IC 43) to maintain adequate cooling at low speeds. On the other hand, for prolonged operation at high speeds above 50 Hz, the shaft mounted fan works well but may make excessive noise. Again, it may be advisable to fit a separately powered cooling fan.
Larger rotating machines can have more elaborate cooling systems with heat exchangers.
The system used to describe the method of cooling is currently being changed by IEC, but the designation system currently in use is as follows:
قصه های قبیله
جذابیت های برق
در ستایش معماری
تکنیک های نورپردازی، مهندسی روشنایی
فکر اقتصادی، کارآفرینی
تکنولوژی های روز دنیا
504 لغت آیلتس IELTS(ضروری برای همه دانشجویان)
شرط پیشرفت+مدیریت زمان و انرژی
اطلاعات علمی ساده و خلاصه
خلاقیت های ناب ناب
کافه کتاب،فرهنگ و ادبیات
رسانه (ایران، بین الملل)
خنده های رنگی رنگی
دیدنی های تو دل برو
دیالوگ های ماندگار
وقایع و تصاویر تاریخی جذاب، گردشگری
ویرایش نشده ها
معرفی نویسنده و مدیر وبلاگ